Design Scope: Depending on client’s water test report
1)Raw water test report:Underground well water
2)RO Purified water capacity:1000L/H
3)RO system recovery : 60%-70%
4)Desalination ratio: 97.3%-98%
5)System working Voltage/Power: 380V 50HZ three phase
6)Feed water Capacity & Working pressure :2000L/H
7)Outlet Purified water standard: TDS<1000PPM ; TDS<2PPM for drinking standard
The purified water system adopts modular design enabling the system to have various characteristics, such as independence,modularization and simple operation, etc. These functions ensure the consecutiveness, stability and reliability of the equipment. In addition,we will make more than two design plans for the selection by the clients in accordance with the water quality report and URS, including pretreatment configuration combined with desalination system,selection of distribution system and disinfection methods, etc. In the mean time, we also provide a complete set of verification system for clients, including design validation in the preliminary stage, FAT test within the factory, installation validation in later stage, operation validation and performance validation as well as perfect after-service system.
system design basis
1.(1) Raw water quality
(2)Inlet water conductivity<150us/cm
2.(1)produce water flow meter:1M3/h water temperature :25℃
(2)Product water quality:WHO drinking water standard
when we got your offer, we will design a plan for you, to make sure the quality of product and delivery .
1.the process of machine will be represent to you twice a week with video and picture,you get all of your machine information.if you have any requirements or some new idea,we do as you wish ,at the same time you can enjoy the professional, considerate service from our engineer and salesman ,which makes your machine perfect.
2.delivery will be timely , we offer the weight of the machine ;the volume of the machine ;the szie of the packing ,the material of package.all of the information about delivery will be collected and provided to you.