Payment & Shipping Terms:
|Membrane:||Reverse Osmosis 4040||Function:||Remove Heavy Metal|
|Capacity:||1000L Per Hour||Material:||Stainless Steel 304|
|Heat Removal Rate:||≥99.9%|
reverse osmosis water treatment plant,
industrial ro plant
Two-stage RO System For dialysis 1TPH High Quality for Pure water Use in pharmacy With EDI Machine
The two-stage reverse osmosis pure water equipment is the first stage reverse osmosis permeate water and then sent to the second stage reverse osmosis system by the second stage high pressure pump to obtain pure water.
Two-stage reverse osmosis pure water equipment process
Original water tank → raw water booster pump → multi-media filter → activated carbon filter → ion softener → security filter → first-stage high-pressure pump → first-stage RO reverse osmosis system → secondary booster pump → secondary RO reverse osmosis system → EDI ultra pure water device (optional) → ozone sterilization equipment (optional) → pure water tank.
Two-stage reverse osmosis pure water equipment features:
1 The original water tank liquid level protection function: If the pure water tank pure water exceeds the high liquid level, the controller turns off the hydration. If the liquid level falls back, restart the hydration.
2 waterless protection function: If the raw water is broken, the controller closes the entire RO system to prevent the pump from pumping. If the water supply is restored, the system is automatically restarted.
3 pure water tank liquid level protection function, such as pure water tank pure water exceeds high liquid level, the controller closes the entire RO system. If the liquid level falls back, restart the system. The two water tanks are interlocked.
3 low-voltage protection function, such as low pressure, close the entire RO system.
4 high voltage protection function, such as high pressure overpressure, the controller closes the entire RO system.
After the tap water is treated by the first-stage reverse osmosis system, the conductivity of the produced water is <10μS/cm, and the conductivity of the produced water after the second-stage reverse osmosis system is <5μS/cm or lower. After the reverse osmosis system, the ion exchange equipment or EDI equipment can produce pure water with a resistivity of 18 megohms (conductivity = 1 / resistivity).
Some time customer when the pure water quality more high and clean, will use EDI System after two-stage RO System,We also have it:
Following is detail of two-stage RO system 1000L/H
|1||Raw water pump Material: stainless steel|
|Including: inlet valve, return valve, pipe, etc.|
|A.tank material:Stainless steel|
|Upper and lower water distributors, central water collection pipes|
|3||Activated carbon filter|
|4||Scale inhibition dosing system|
|A. Flow rate 1.0L/H Head: 35M|
|B. Dosing bucket 40L (PE)|
|C. Debugging pharmacy|
|5||5μm security filter|
|Model: 5 cores Village quality: stainless steel|
|B.20′′×5μm PP filter|
|6||First stage high pressure pump|
|Two-stage high pressure pump|
|7||Two-stage reverse osmosis unit Water production: 1m3/h, salt rejection rate: 96～99%, system water utilization rate: ≥60%|
|Include||A, membrane module 4040-1 material: stainless steel|
|B, membrane element RO-4040|
|8||Connecting pipe fittings, valve stainless steel|
|9||Electronic control system (automatic control)|
|Total control cabinet: automatic controller control, water level sensor, Korean pressure controller, time controller.|
|A, clean water quartz sand|
|B. Coconut shell activated carbon for drinking water|
|A, reverse osmosis pressure gauge 0 ~ 25kgf / cm2|
|B, high pressure pump low voltage protection switch|
|C, system pressure gauge 0 ~ 7kgf / cm2|
|D, reverse osmosis water conductivity meter|
|E, automatic controller (RO-PLC)|
|A, water flow meter (panel type)|
|B, concentrated water flow meter (panel type)|
Picture of two-stage RO System:
Back Picture of two-stage RO System:
Picture of EDI System:
Contact Person: Abby