Payment & Shipping Terms:
|Item:||1500LPH RO Water Treatment Plant For Purified Water Dialysis / Hospital||Raw Water:||Seawater|
|Output:||1500L Per Hour||Material:||Fiber Reinforced Polymer|
1500 LPH RO Water Treatment Plant,
Polymer RO Water Treatment Plant
1500LPH RO Water Treatment Plant For Purified Water Dialysis / Hospital
Is a kind of single stage reverse osmosis equipment by means of choice through (through) membrane function to pressure as the driving force
of membrane separation technology, when system and the pressure is greater than in the aqueous solution of osmotic pressure, the water
molecules through the membrane unceasingly, after producing water flows into the central tube, and then out in the end the impurities in the
water, such as ion, organic matters, such as bacteria, viruses, interception on the inlet side of the membrane, and then in the thick water
outflow water end, so as to achieve separation and purification.
Cleaning method of single-stage reverse osmosis equipment:
It is generally cleaned once every 3~12 months. If it has to be cleaned once every month, it indicates that the pretreatment system should be
improved and the operation parameters should be adjusted.
If cleaning is needed once every 1 to 3 months, the operation level of the equipment needs to be improved, and it is difficult to determine
whether the pretreatment system needs to be improved.
Raw water → raw water tank → raw water pump → multi-medium filter (quartz sand filter) → activated carbon filter → soft water processor
(add scale inhibitor device) → precision filter → high pressure pump → primary reverse osmosis (RO) device → ULTRAVIOLET sterilization
device (ozone sterilization device) → water point.
Contact Person: Jessie