Payment & Shipping Terms:
|Product Name:||Purification Equipment||Material:||Stainless Steel|
|Type:||Mobile Purification System||Certificate:||CE ISO|
|Recovery Rate:||65-75%||Desalination Rate:||99%|
sea water purification machine,
salt water purification system
Reverse Osmosis System Purified Drinking Water Machine Water Desalination Plant Price
For a specific water treatment system, Chunke pure water treatment manufacturer believe that the long-term stability of its performance is indispensable. The success of the long-term performance of the RO system depends on normal operation and maintenance, including the commissioning of the entire system, starting operation and shutdown. , Cleaning and maintenance, membrane surface dirt and scale prevention should not only be considered in the pretreatment design, proper operation is also extremely critical. At the same time, the preservation of records and daily reports of RO operating parameters are very important. These data can reflect the system's The actual operation situation is also a reference when taking corrective measures.
Customized size of the system
|Outlet water conductivity
|Raw water conductivity
Details of the water purification equipment
The system is installed into a 40ft container,which is convenient for on site installation.We will decorate the container
A.Ventilation system: 1 air conditioner, 1 exhaust fan, 2 wall fans
B.Fire protection equipment: 3 fire extinguishers, 1 set of fire alarms
C.Renovation instructions: white paint is sprayed in the container, 4 mm thick aluminum skid plate is placed on the container floor, 4 fluorescent lamps are installed on the ceiling, and 6 waterproof sockets are installed on the container wall.
Electric Control System
The total control cabinet: Japan Mitsubishi PLC programmable controller automatic control, Taiwan Wei Lun 10.2-inch large screen true color man-machine interface touch screen, France Schneider Electric components, RO membrane automatic washing, the original water tank and pure water tank water level control automatically stop , Low voltage, high voltage, overheating, overcurrent, phase protection and alarm function, pre-installed remote monitoring interface.
Care and maintenance of reverse osmosis equipment
1. After the water is produced in each shift, the reverse osmosis components should be protectedly washed for 20 minutes.
2. As the running time increases, the surface of the membrane will adhere to the sediment, which affects the amount of water permeability. It is necessary to periodically clean the RO element. According to different pollution conditions, targeted treatment.
3. The high-pressure pump should be checked and repaired frequently, and the lubricating oil should be replaced in time according to the requirements of the equipment manual.
4. Regularly inspect and check the conductivity meter and pressure gauges to make them work normally and accurately.
5. The RO device will be shut down for a short period of time (no more than 3 days). It can be flushed for 0.5 hours at low pressure every day with the security filter and the module is filled with water.
6. If the RO device is shut down for a long period of time (> 3 days), 1% formaldehyde solution should be used to fill the RO components, and then all valves should be closed, and checked once a month. In summer, control the ambient temperature to prevent mildew and prevent freezing in winter. When adding 10-20% glycerin.